BG-C440F Innovation Manual Call Point (MCP) is non-addressable. It alarms by the current caused by pressing the action plate. It can be simply connected to compatible conventional fire alarm system from various manufacturers. This MCP is suitable for public places. When there is fire, pressing the action plate on this MCP can send alarm signal to compatible conventional fire alarm control panel.
- Alarming by pressing, reset by a special key
- Plug-in structure.
- Designed to comply with EN 54-11.
|Operating Voltage||24VDC (12VDC~28VDC)|
|Alarm Current||≤30mA(equivalent resistance is 470Ω/1W)|
|Indicator||Red. Illuminates after alarming.|
|Type of Initiating Part||Reusable|
|Initiating Mode||Pressing the action plate manually|
|Resuming Mode||Manually resumed by a special key|
|Class||Type A, indoor use|
|Ingress Protection Rating||IP43|
|Relative Humidity||≤95%, non condensing|
|Material of Enclosure||ABS|
|Dimension (L×W×H)||87.1mm×87.1mm×58mm (with back box)
87.1mm×87.1mm×23mm (without back box)
|Mounting Hole Distance||60mm|
|Weight||About 160g (with back box)
About 107g (without back box)/td>